SOLAR PV INSTALLATIONS AND REPAIRS
Solar PV installations are just one of the many services we offer. Whether it is an in-depth solar PV repair or just a general maintenance repair, our skilled team can rectify all the problems with your system. we have designed, installed and maintained solar systems for large commercial companies as well as supplying advice when needed. When you want a reliable company to visit your home or business to fit a solar system, contact us in Yateley, Hampshire.
SOLAR PV SYSTEMS
To ensure that your solar PV system is working effectively, our expert electricians travel to your company to assess the system and make any necessary changes to it. At our company, we have completed many jobs in both the commercial and domestic sector, and when you need general advice regarding solar PV systems, please do not hesitate to contact us.
SOLAR PV SYSTEMS – FAULTS
As part of our solar PV System service, our team assesses the system and repairs any faults that may have arisen. We also offer advice on the work that needs to be undertaken to repair the fault. You can rely on us for a convenient service as in our warranty repairs solution, we contact manufactures to source parts, and then our skilled team repair any faults to ensure your system is back to full production.
Below is a brief outline of one of the many commercial systems we have repaired
The video below demonstrates a medium-sized commercial installation we were asked to report on and subsequently rectify the system due to poor installation, wrongly configured array and damaged inverter along with a poor Electrical install providing continuous tripping of the main RCD due to segregation issues.
After two days onsite the panel configuration had been completely balanced with the addition of an extra string to keep well within the inverters tolerance levels and provide optimum performance.
A new 3 phase distribution board had been installed back to the busbar chamber providing complete segregation and eliminating any nuisance tripping of the main RCD, I also installed a new inverter and replaced the AC isolator due to a broken terminal causing heat damage from arcing.
To complete the install a cable tray was installed on the outside of the building to support the DC cables previously left hanging and unsupported, and in addition, fire sealed the cable entry into the building along with the testing and inspection an installation certificate was issued and the owner was very happy.
I have remained in contact with the customer in the months since completion of this work and have received great reports of the system's production and performance after the completion of my work.
If you have a Solar PV system which is not performing as expected or develops a fault give Lee a Call 01252 414041